Калькулятор микроклимата в шкафу.
Для получения расчета тепловыделения шкафа и подбора рекомендованного оборудования, заполните необходимые поля формы.
Select the cabinet material from the list or set the heat transfer coefficient of the material manually
Note if heat transfer through the cabinet roof is difficult
For the selection of equipment, the overall dimensions, material and location of the cabinet are required..
Specify the minimum and maximum ambient temperature
Note if additional humidity control is required
Specify the maximum possible relative humidity of the environment and the temperature at which it is reached
Specify cabinet operating altitude above sea level to determine air density
Enter the total heat output generated by the equipment inside the cabinet. Preliminary calculation of the generated thermal power can be carried out according to the following rules: • Frequency converters — 5% of the power consumed • Power supplies and transformers — 10% of the power consumed • Automatic breakers - 20% of current draw • Starters - 40% of draw current Use data provided by installed equipment vendors to accurately determine heat loss.
Specify the allowable temperature range in the cabinet.
Specify the maximum allowable relative humidity in the cabinet. The recommended maximum humidity in the cabinet is no more than 65%.
Specify the operating conditions and desired cabinet parameters for equipment recommendations
Specify the parameters of the electrical network of the cabinet for the selection of equipment.
Specify the operating conditions of the cabinet.
We will contact you shortly